|Intervolve Advisory - #10061|
( 509 d 17 h 50 m ago)
|Start||29/03/2018 06:00 AM ACDT|
|End||29/03/2018 08:16 PM ACDT|
|Summary||Site UPS Maintenance (Secondary/B Feed)|
|Areas||Adelaide - Pooraka|
During the window, contractors will be performing the replacement of fans and DC capacitors of the UPS providing power to the secondary or "B" feed of DC1 & DC2 as part of regular preventative maintenance.
UPDATE: 29/03/2018 15:26:42 GMT+10:30 ACDT
Scheduled UPS maintenance has been completed successfully and all systems are operating as normal. Should you require any further information or assistance, please contact our Support team on 1300 664 574, or by email on email@example.com.
UPDATE: 29/03/2018 17:51:36 GMT+10:30 ACDT
Emergency Hazard Update: Unfortunately, recent maintenance to the B unit UPS has resulted in a software freeze of the unit's control system. Whilst the power feed has not been impacted, the unit requires to be placed into maintenance bypass to diagnose the issue. Specialist technicians are on site to perform the required diagnostics. This update is issued as a HAZARD warning only as impact to the IT load is not anticipated. Updates to follow, on completion of diagnostics.
UPDATE: 29/03/2018 20:19:00 GMT+10:30 ACDT
Technicians have completed diagnostics and elected to cycle in a standby UPS unit whilst the original B unit is inspected. Bypasses have been removed and all IT load at the facility is fully protected.
Return to Service Outage Advisory list