|Intervolve Advisory - #10080|
( 1027 d 9 h 33 m ago)
|Start||28/11/2018 03:00 AM ACDT|
|End||28/11/2018 03:35 AM ACDT|
|Summary||Cooling Issue - DC1|
|Areas||Adelaide - Pooraka|
Elevated supply temperatures were noted underfloor on the south side of the DC1 suite due to a CRAC unit malfunction.
The standby unit has been brought online and all temperatures were returned to below threshold values within 35 minutes.
Engineers are onsite and undertaking repairs to the unit that faulted.
If you have any concerns or queries, please contact our Support team on 1300 664 574 or by email on email@example.com
UPDATE: 28/11/2018 07:00:10 GMT+10:30 ACDT
Temperatures returned to within normal thresholds at 3:35am and as of 7:00am continue to remain at desired levels.
Return to Service Outage Advisory list